Roof heat pump unit noise control project: Most of the […]
Roof heat pump unit noise control project: Most of the bathing centers use a central hot water system, and the roof air source heat pump unit operates 24 hours a day to generate noise and affect the daily life of the surrounding residents. After the noise reduction process, the Hanks technicians reduced the nighttime noise measurement from 55dB to less than 35dB (almost no heat pump unit noise). The following treatment methods are summarized for your reference.
The noise reduction problem of heat pump unit is mainly from three aspects: air sound, equipment vibration and pipeline vibration.
1. Airborne noise reduction requires special treatment for sound insulation. If the pump set is separated from the owner by only one floor, the common method is to add sound insulation cover and noise elimination equipment.
2, system vibration isolation, generally installed in the bottom of the pump body metal damping material shock absorber. (The natural frequency and load-bearing capacity of the damper are designed according to the field data analysis)
3. Pipeline vibration reduction, the connection between the general pipe and the ground is hard connection, which causes the pipe vibration to pass directly to the building structure, and the elastic support is installed under the pipe, which can better prevent the vibration energy from propagating to the building structure.
When the heat pump noise is used for construction, it is necessary to consider the influence of outdoor extreme weather. The noise reduction equipment should try to reduce the noise, wind pressure and anti-corrosion effect.